Question about Heating & Cooling
The furnace goes through it's process...the last being the blower coming on. However, the blower isn't kicking on. Sometimes if I turn it off and on at the thermostat, I can get it to re-cyle and then the blower will come on. It's sporadic, but it's happening more frequently. I temporarily remedied the situation by turning my blower to the on mode, as opposed to the auto mode. But I hate to run the blower all the time. Any ideas? Thank you!
My guess is the FAN RELAY has loose contacts in it Trace the wires from the motor to where they tie in 1 will go to the power cord (this in L2 or Nut) The other 1 or 2 wires will go to a fan swich/relay or a rotary hi limit fan acutator sw. This rotary fan sw has a lot of cousins. On some Carrier Bryant Paynes and or Day Night furnaces that are over 20 years old the fan switch is a small rectangular cube with a seperate heater inclosed in the rectangular box. This fan sw could also be your problem but Im betting on the fan relay. It usually Click when you turn the Fan from auto to on. And the wire G goes to it (eventually)from the thermostat. CHeck this when its acting up. You could jump around the relay going from the L1 feed on the relay to the Closed motor speed.
I doubt you have a bad fan motor. But I could be wrong. Usually they have a smell associated with a bad one and you dont mention this.
Posted on Mar 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2015 | Heating & Cooling
Jan 02, 2014 | Heating & Cooling
Nov 22, 2011 | Aprilaire 550 Humidifier
Sep 16, 2011 | Heating & Cooling
Jan 31, 2011 | Dayton Gas Furnace Heater
Jan 14, 2011 | Goodman GMS90703BXA Heater
Feb 26, 2010 | Heating & Cooling
Dec 04, 2009 | Omega Trane Furnace Draft Inducer Blower...
Feb 06, 2009 | Carrier Heating & Cooling
Jan 16, 2009 | Heating & Cooling
Feb 21, 2017 | Heating & Cooling
419 people viewed this question
Usually answered in minutes!