Question about Culligan Sediment Water Filter
My iron-cleer system has never done this until today. Water is constantly draining out of the discharge tube and no it is not regenerating, is there a purge valve on the system that I cant find?
It normally is under pressure. There is a "check ball" in the tube to prevent water from coming out of the tube in service. The feed tube has to be flooded with water in service position so when system goes in to draw cycle vacuum is created in the tube to draw bleach. You may have a plugged eductor assembly or feed tube may be restricted.
Posted on Aug 17, 2011
Iron cleer and sulfur cleer systems have a bed life of 750000 ppm. This is generally about ten years. You can try running the system every day for 1 week to see if it improves. The air pump may not be working properly so iron and h2s may not be being oxidized properly. H2S smell would be the first symptom of this. I would suggest a service call.
Posted on Jun 29, 2011
Tips for a great answer:
Jul 30, 2011 | Culligan Under Sink Water Filter
Mar 28, 2011 | Culligan 34" Whole House Water Filter...
Jan 30, 2011 | Culligan Sediment Water Filter
Jan 28, 2011 | Culligan 34" Whole House Water Filter...
Jan 08, 2011 | Culligan Sales #SY-750S Under Sink Water...
Dec 17, 2010 | Culligan Under Sink Water Filter
Jul 25, 2010 | Culligan Sediment Water Filter Heavy Duty
Jun 10, 2010 | Culligan Under Sink Water Filter
May 15, 2010 | Culligan Under Sink Water Filter
Nov 09, 2009 | Culligan Sediment Water Filter
Aug 04, 2014 | Culligan Sediment Water Filter
993 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: