Question about Culligan Sediment Water Filter
My iron-cleer system has never done this until today. Water is constantly draining out of the discharge tube and no it is not regenerating, is there a purge valve on the system that I cant find?
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It normally is under pressure. There is a "check ball" in the tube to prevent water from coming out of the tube in service. The feed tube has to be flooded with water in service position so when system goes in to draw cycle vacuum is created in the tube to draw bleach. You may have a plugged eductor assembly or feed tube may be restricted.
Posted on Aug 17, 2011
Iron cleer and sulfur cleer systems have a bed life of 750000 ppm. This is generally about ten years. You can try running the system every day for 1 week to see if it improves. The air pump may not be working properly so iron and h2s may not be being oxidized properly. H2S smell would be the first symptom of this. I would suggest a service call.
Posted on Jun 29, 2011
Tips for a great answer:
Jan 06, 2016 | Nuova Simonelli Premier Maxi Espresso...
Jun 19, 2014 | Whirlpool Water Dispensing & Filtration
Feb 05, 2014 | Reliance Water Dispensing & Filtration
Sep 03, 2011 | Home
Jul 30, 2011 | Culligan Under Sink Water Filter
Jun 17, 2011 | Heating & Cooling
Jul 25, 2010 | Culligan Sediment Water Filter Heavy Duty
Jan 24, 2010 | Culligan Sediment Water Filter Heavy Duty
Nov 09, 2009 | Culligan Sediment Water Filter
Apr 04, 2009 | Aprilaire 550 Humidifier
Aug 04, 2014 | Culligan Sediment Water Filter
1,063 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: