Displaying "Co" code, and running when turned off with the remote
We also have the LG Art cool. It is displaying the code" Co", which i haven't seen before. We too have had the "C6" code before. Although the unit is turned off at the remote, it is still running with the "Co" code on the unit display
An expert who has achieved level 2 by getting 100 points
An expert that got 10 achievements.
An expert that got 5 achievements.
An expert whose answer got voted for 100 times.
Re: Displaying "Co" code, and running when turned off...
It sounds like you have lost communication between the indoor and outdoor units. This can be one of two things. Either the connection indoor or outdoor is loose or bad, or a rat may have eaten the cable in cieling.
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Nov 3, 2009 - Air conditioning (Accent Air control panel) is displaying EC - what ... Panasonic mini split air conditioner css9nkua error code h99 what does it mean ...ERROR CODE ON AIRCONDITIONER LG ART COOL INVERTER MODEL .
I may not be of much help but I may be able to guide you into some diagnosos. If there is a communication problem between the inside and outside unit, both on the inside and outside units a colored LED will bling 5 times then pause for 3 seconds. The 33 and 44 codes are confusing to me because I have never seen this. Try resetting the outside unit with no call for heat or cool from the inside unit. After about 20 seconds, restore power to the outside unit. Go in and turn on the remote and make sure you lower the cool setting more than degrees cooler than the room temp. After 3 minutes the outside unit should turn on. If you get an error code of either 1, 2 or 5 blinks document it for the technician. If you continue to get your 33 and 44, you have a bad control board.
If all else fails, press and hold the button located on the lower left side of the art unit and hold for about 5 seconds. If it still no longer works, now you will need the help of someone who knows these units.