Question about Jandy Laars LX Pool Heater / 400,000 BTU / Natural Gas
The heater will cycle light and gas will run as ssoon as full gas flow starts it turns off. the cycle repeat for two or three times then nothing
The most likely cause is a defective limit switch on the header. There are two limit switches, a "high limit" and a "low limit". They are mounted in wells next to brass plugs in the thermoplastic header just below where the water outlet is. They have shiny metal covers over them and you can see the wires going into the wells just below each cover. With time and use the brass plugs begin to seep pool water, corroding the sensors. If the sensors are open circuited the ignition controller will not allow the hot surface ignitor to fire the gas. Even though this is a failure of the limit switch it will show up on the diagnostic panel as "AGS" (automatic gas shutdown) because it is not a temperature limit problem but an "ignition problem."
Posted on May 18, 2009
Posted on Feb 27, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 17, 2014 | Teledyne Laars Laars Lite 2 Pool Heater...
Aug 17, 2013 | Teledyne Laars Laars Lite 2 Pool Heater...
Oct 21, 2012 | Teledyne Laars Laars Lite 2 Pool Heater...
Apr 01, 2010 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 26, 2008 | Raypak Pool Heater Covers for Teledyne &...
679 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: