Question about Goodman Heating & Cooling
My furnace will only kick on about once an hour unless i turn the thermostat off and back on. also the water will not flow out unless i crimp the run-off hose thing. it will keep running if i take the door off the electronic air cleaner and let it have more air flow to it. also, i do not get near the force of air from my vents as i did last year. i havent had much luck on a real diagnosis. i was told i need bigger vents, but the way i see it is they havent changed since the furnace was installed in 1998, so that cant be the issue now. oh, the furnace is a Janitrol by Goodman. Any feedback would be appreciated.
Your unit is starving for air. Either you have a dirty pre filter before the EAC (Electronic Air Cleaner) or the EAC needs to be cleaned. Or the A Coil is clogged up which needs cleaning. Have you ever cleaned the small pre filters ahead of the EAC? How about the EAC have you taken the EAC out and washed the plates off? I am just suggesting some feedback here so bear with me. ken
Posted on Feb 27, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 16, 2014 | Heating & Cooling
Oct 12, 2013 | Heating & Cooling
Feb 21, 2013 | Bryant Cube Series 1 Stage Heat/ 1 Stage...
Sep 25, 2011 | Dometic Rooftop RV Air Conditioner
Sep 16, 2011 | Heating & Cooling
Jan 18, 2011 | Heating & Cooling
Oct 29, 2010 | Heating & Cooling
Jan 09, 2010 | Amana Heating & Cooling
186 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: