Question about Heating & Cooling
I purchased an lg minisplit heat pump system over the summer and installed it in August and it cooled great. When it was put into the heat mode, it was blowing cold air. I found the reversing valve not energizing. I replaced the board on the outdoor unit. Now when the system is put into the heat mode, you can hear the reversing valve energize but nothing else happens except the indoor blower comes on and runs for about 10 seconds. I cannot find any technical manuals or any place to get help.
You may want to check that the pressure switch is not functioning? Secondly there is also a thermo sensor on the condenser coil which could be faulty.
Posted on Mar 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 24, 2015 | LG Heating & Cooling
Dec 02, 2013 | LG LSN122HE / LSU122HE - 11,500 BTU 13...
Mar 13, 2017 | Heating & Cooling
Nov 15, 2012 | Soleus Air KFHHP-22 22000 BTU Mini Split...
Sep 12, 2011 | LG LS-L1210CL Mini Split Air Conditioner
Nov 05, 2010 | Goodman PHKJ048-1 Air Conditioner
Jul 25, 2009 | Heating & Cooling
Mar 07, 2009 | Soleus KFR12GWD 12,000 BTU Heat & Cool...
1,097 people viewed this question
Usually answered in minutes!