Question about Cutler Hammer 1 Pole 15 Amp Ground Fault
A Cutler-Hammer Ground Fault circuit Breaker Type GFCB - Type HAGF trips each time a load is applied. If the circuit is changed out to a regular (non- ground fault) circuit breaker the load will not cause the circuit breaker to trip. The circuit is for 6 outside receptacles app. 100 feet of 12/2 w/ ground Romex wire.
The most likely causes in their order of probability are: 1) water somewhere in the circuit causing the hot wire to ground; 2) a legitimate trip caused by a defect in a device plugged into the circuit; and 3) a defective GFCI breaker. In the first case, wait until it has been dry for about a week and see if it trips. In the second case, make sure there is nothing plugged into the circuit and try resetting. In the third case go ahead and put the regular breaker in, then put a GFCI outlet into the first box downstream from the breaker. If installed according to the directions, that outlet should protect all of the outlets downstream.
Posted on Feb 27, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 11, 2015 | Electrical Supplies
Aug 25, 2013 | Electrical Supplies
1,162 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: