Question about Aprilaire 700 Humidifier
My Aprilaire 700 is producing about 1 gallon of water/minute of operation-whats wrong?
There is a small oriface that is installed next to the solenoid valve. It sounds like this oriface is missing. It reduces the water flow through the humidifier when it is working properly. You should be able to disassemble the solenoid fittings to check and see if the oriface is in the water line. For a "temporary" fix regulate the water pressure down by closing down on the saddle valve.
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 13, 2015 | Aprilaire Humidifiers
Dec 29, 2010 | Aprilaire 700 Humidifier
Nov 17, 2010 | Aprilaire 700 Humidifier
Dec 13, 2009 | Aprilaire 700 Humidifier
Jan 16, 2009 | Aprilaire 700 Humidifier
Jan 12, 2009 | Aprilaire 700 Humidifier
Oct 19, 2008 | Aprilaire 700 Humidifier
Dec 24, 2007 | Aprilaire 700 Humidifier
288 people viewed this question
Usually answered in minutes!