Question about Goodman Heating & Cooling
The unit was running for about 10 or 15 min , I realized what i did and shut it down. If I reclaim all refridgerant. Can I just recharge with r22?
Do a triple evac. Reclaim, flush with r22, reclaim, flush with r22, reclaim, flush with r22, reclaim. install afilter drier. Evac down to at least 200 microns. Recharge. you should be ok.
My concern would be disposing of the old "now blended" refrigerant
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 11, 2015 | Goodman Heating & Cooling
Oct 02, 2014 | Cfm Daikin R410a Split System Air...
Apr 20, 2014 | Fedders A7DH45B2A Dehumidifier
Sep 09, 2011 | Breezaire WKE 6000 Wine Cooler
Jun 27, 2011 | Kohler 12 kW Emergency Power System -...
Feb 03, 2011 | Heating & Cooling
Jun 19, 2010 | Whirlwind FH-778 Air Conditioner
May 19, 2010 | Carrier 38CKC036 Air Conditioner
Aug 20, 2009 | Carrier Heating & Cooling
Jun 09, 2009 | Whirlwind FH-778 Air Conditioner
183 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: