Question about Goodman Heating & Cooling
The unit was running for about 10 or 15 min , I realized what i did and shut it down. If I reclaim all refridgerant. Can I just recharge with r22?
Do a triple evac. Reclaim, flush with r22, reclaim, flush with r22, reclaim, flush with r22, reclaim. install afilter drier. Evac down to at least 200 microns. Recharge. you should be ok.
My concern would be disposing of the old "now blended" refrigerant
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 21, 2015 | Heating & Cooling
Oct 25, 2011 | Heating & Cooling
Jun 13, 2010 | Lite On Laars Lite 2 Heaters: 250,000BTU...
May 13, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Feb 16, 2010 | Heating & Cooling
Apr 23, 2009 | Goodman GMS90703BXA Heater
Dec 10, 2008 | Reddy Heater-30-55,000 BTU Variable
Dec 04, 2008 | Reddy Heater-30-55,000 BTU Variable
Nov 01, 2008 | Reddy Heater-170,000 BTU Kerosene Deluxe
179 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: