Question about Gb Electrical 100 Amp GE Load Center
Have two apt bldgs built in 1969. Both have same size breaker box in kitchens. Size is 10 3/16 X 17 5/8. One bldg. is 60amp and one is 100amp. Want to find "guts" to upgrade. Numbers on 100amp box are 0270 P-0122; Flush Typ TM1410F; replacement parts neutral 456C245G4. Numbers on 60amp box are 1269 P-0114; Flush Typ TX1412F; replacement parts 456C245G3 I don't know which are Model numbers. I have searched all over to no avail. I can't even find a product support help for electrical equipment for G.E.
You won't find any "guts", like longer busbars, to upgrade. The panels pre-date most of the codes and you will not find replacement parts, except maybe a breaker or two. For panels that old you are looking at the possibility of having aluminum wiring and/or two conductor wiring (hot and neutral). In either case, your local code office or utility company will probably require you to update to current requirements. You cannot connect aluminum to copper without nickel connectors because of galvanic corrosion, and if you are disturbing any of the wiring you will probably need to upgrade to three conductor (hot, neutral, and ground). You should be able to buy "Square D" HOM series replacement panels with breakers for about $120 or less.
--Peter Nomikos, ICC Master Code Professional
Building and Zoning Director, City of Mauldin, SC
Posted on Feb 26, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 25, 2017 | Kenmore Kitchen Ranges
May 10, 2017 | Electrical Supplies
Jan 05, 2015 | Electrical Supplies
Aug 05, 2012 | Electrical Supplies
Sep 07, 2011 | Cutler Hammer 100 Amp Main Breaker...
Oct 24, 2010 | Gb Electrical 100 Amp GE Load Center
Aug 10, 2010 | Eaton ARC FAULT CIRC BREAKER
Mar 26, 2010 | Cutler Hammer 100 Amp Main Breaker...
Mar 14, 2010 | Gb Electrical 100 Amp GE Load Center
Dec 16, 2009 | Cutler Hammer Electrical Supplies
1,220 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: