Question about Weather King 10AJA6001AH Air Conditioner
ONE YEARS AGO WE INSTALLED A 2TON 10 SEER WEATHERKING HEAT PUMP... this past summer I had to replace the compressor????? I know the charge was correct. How ever I noticed the compressor did not have a heater. Thinking this was the reason the compressor failed I installed a band type heater on my newly installed compressor. A friend of mine is stating I should have traps on the suction line.I have approx 20' of vertical rise total length no more then 60' .After approx. 10 to 15mins of operation the indoor and outdoor unit begins to vibrate along with a loud noise..... Help
Your friend is correct. Installing a sump or p-trap in the suction line will probably help. The oil may be leaving the compressor but can't get back.
Posted on Feb 24, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 28, 2015 | Heating & Cooling
Feb 14, 2015 | Goodman Heating & Cooling
Feb 14, 2015 | Amana Goodman R-410A Heat Pump Condenser 2...
Jan 12, 2015 | Protech Rheem Ruud Weatherking Factory OEM...
Oct 25, 2013 | Goodman Manufacturing...
Jun 29, 2017 | Goodman GMS90703BXA Heater
Jan 26, 2011 | Heating & Cooling
Aug 31, 2010 | Weather King 10PJA2501AH Air Conditioner
May 01, 2009 | Ruud UAMB Air Conditioner
334 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: