Question about APC MasterSwitch Power Receptacle - Power distribution strip- 4 Output (ap95103202) UPS System
I am assuming that you installed your receptacles by attatching one wire to one screw .. not pigtailing the wires to the receptacle. It seems to me that your second receptacle has a missing link. Look at the sides on the receptacle, there should be a small link between the two terminal screws to carry the power to the next in line. If the link is missiong then replace that receptacle and you will be good ion the circuit .. If the link is there , then check you connections, sometimes we can catch a bit of the insulation in the terminal and then there is no transfer of electricity from that point on .. If you pigtail the wires and then connect the receptacle to the tail, then the circuit has more integrity. and we should always use the screw terminals, not the stab-ins. a better , more secure connection.
Posted on May 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 04, 2016 | Square Electrical Supplies
Aug 31, 2014 | Electrical Supplies
Dec 06, 2013 | Eaton ARC FAULT CIRC BREAKER
Feb 23, 2013 | Dryers
Jul 04, 2012 | Electrical Supplies
May 27, 2011 | Intermatic T104P 208-277Volt 40-amp Timer...
Jan 23, 2011 | GE Hammering
Apr 24, 2010 | Hammering
Apr 16, 2009 | 2001 Chrysler Town & Country
May 30, 2007 | Windsor SR12 Sensor Bagged Upright Vacuum
265 people viewed this question
Usually answered in minutes!