Question about APC MasterSwitch Power Receptacle - Power distribution strip- 4 Output (ap95103202) UPS System
I am assuming that you installed your receptacles by attatching one wire to one screw .. not pigtailing the wires to the receptacle. It seems to me that your second receptacle has a missing link. Look at the sides on the receptacle, there should be a small link between the two terminal screws to carry the power to the next in line. If the link is missiong then replace that receptacle and you will be good ion the circuit .. If the link is there , then check you connections, sometimes we can catch a bit of the insulation in the terminal and then there is no transfer of electricity from that point on .. If you pigtail the wires and then connect the receptacle to the tail, then the circuit has more integrity. and we should always use the screw terminals, not the stab-ins. a better , more secure connection.
Posted on May 04, 2010
Tips for a great answer:
Jan 09, 2014 | APC UPS Battery Backup Systems
Nov 28, 2013 | UPS Battery Backup Systems
Nov 28, 2013 | MGE NOVA AVR 1100VA Tower UPS 81111 UPS...
Feb 14, 2013 | UPS Battery Backup Systems
Feb 03, 2010 | APC Conext 900VA (cnb900) UPS System
Jan 29, 2010 | APC MasterSwitch Power Receptacle - Power...
Jun 04, 2009 | Panamax MAX 1500-UPS (M1500UPS) UPS System
Jun 26, 2008 | Dynex (TE685AVR) UPS System
Jan 18, 2006 | APC MasterSwitch Power Receptacle - Power...
264 people viewed this question
Usually answered in minutes!