Question about Heating & Cooling
Yep, thats where the lweak is. try to loosen the three screws and adjusting it to getgood seal from o-ring behind inducer motor.
Posted on Mar 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 02, 2015 | Ruud RGPS10EBRGR Zephyr 100K BTU 80%...
Feb 22, 2015 | Goodman Manufacturing GMVC951155DX 95%...
Nov 13, 2014 | Rheem Classic Series 95% Two-Stage Upflow...
Jan 26, 2013 | American Standard Trane Ge Gas Furnace...
Mar 10, 2011 | American Standard Heating & Cooling
Hi, Basic Furnace or Heating System Troubleshooting
Check on the inside of the bottom cover to see what the two blinks means
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 02, 2011 | Heating & Cooling
Dec 05, 2010 | Heating & Cooling
Mar 03, 2010 | Heating & Cooling
375 people viewed this question
Usually answered in minutes!