Question about Air Conditioners
Yep, thats where the lweak is. try to loosen the three screws and adjusting it to getgood seal from o-ring behind inducer motor.
Posted on Mar 12, 2009
Tips for a great answer:
Feb 18, 2016 | Filter Air Conditioners
Dec 02, 2015 | Ruud RGPS10EBRGR Zephyr 100K BTU 80%...
Jan 26, 2013 | American Standard Trane Ge Gas Furnace...
Aug 28, 2011 | American Standard Air Conditioners
Jun 21, 2011 | Air Conditioners
Mar 10, 2011 | American Standard Air Conditioners
Mar 02, 2011 | Air Conditioners
Hi, Basic Furnace or Heating System Troubleshooting
Check on the inside of the bottom cover to see what the two blinks means
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 02, 2011 | Air Conditioners
Oct 29, 2010 | American Standard Air Conditioners
Oct 27, 2009 | Air Conditioners
371 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: