Question about Ruud Central System Air Conditioner
My thermostat is installed in a small hallway just before entry into master bedroom which is only room on that side of house. When the heat is on the other side of house is to cool and when Ac is on the other side is warm. There is a large living room then entry into a hall way with 3 bedrooms. I have always felt that the thermostat should be mounted in the living room or in the other hallway. The return air is right below the thermostat.
You need to balance the system. It's a matter of adjusting the dampers or registers so that you have a little less air flow near the T-stat and more to the other end of the house. Likely you have a return vent near the T-stat. That return draws air to it and likewise the T-stat. If you are getting a lot of air out of the registers on that end of the house damper them to force more air to the other end of the house. Do not close them entirely though. You may have to play with it a little to get it right. I hope this helps. Please remember to rate Fixya rate me.
Posted on Feb 23, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 10, 2007 | Sharp CV-P09FX Air Conditioner
on May 25, 2015 | Heating & Cooling
Mar 03, 2011 | Heating & Cooling
Jul 30, 2009 | Maytag Portable Air Conditioner M6P09S2A
May 26, 2009 | Heating & Cooling
Jan 23, 2009 | Heating & Cooling
Aug 06, 2008 | Heating & Cooling
Aug 01, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
152 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: