Question about Heating & Cooling
The outdoor coils getting some frost on them is normal. However the system should periodically (every 30-90 mins of run time) go into "defrost" mode. Essentially it reverts back to cooling and shuts off the outdoor fan. This heats the coil outside to melt the frost. You may see some steam at this time also. Again normal. If this is not happening or not happening often enough the coil will ice up. Inside the outdoor unit is the defrost board. There is usually a pin setting for either 30-45-60 or 90 minutes. Make sure you kill the power to the unit before sticking your hands in there. Check to see what setting your is on and lower it one peg. If it's been colder and/or more humid you may need to cycle sooner. Good luck I hope this works for you. Please don't forget to give me a Fixya rating.
Posted on Feb 23, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 19, 2016 | Frost Refrigerators
Feb 13, 2015 | Heating & Cooling
Oct 18, 2012 | Kelvinator Refrigerators
Jan 04, 2011 | Heating & Cooling
Oct 12, 2010 | Whirlpool 19.6 cu. ft. Upright Freezer...
Dec 29, 2009 | Intertherm P3RC-030K Air Conditioner
Nov 25, 2009 | Refrigerators
Aug 28, 2009 | Kenmore 60721 Refrigerator
Jun 09, 2009 | Refrigerators
Jun 14, 2008 | Kenmore Freezer 20.3 cu. ft. Frost Free...
May 22, 2017 | Heating & Cooling
127 people viewed this question
Usually answered in minutes!