Question about Intermatic EI210 Electronic Auto Shutoff Timers
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You could try disconnecting power to the switch for a few minutes maybe that will reset it. Other than that I would say cut your losses and replace it. Hope this helps a little.
Posted on Dec 04, 2008
reading the specs i should say its a timer for only one zone. you can use it for one zone switching or for the pump. sorry.
Posted on Feb 14, 2010
The wires on your new switch are intended for black = power .. white = neutral . and red = lights .. with two black wires on the old switch I am assuming that there is a bundle of white wires in that wall box, the white timer needs to join that bundle ... then you need to determine which black wire is the power from the electrical panel ( voltage tester) and connect to the black timer wire .. the red timer wire connects to the other black wire in the wall..
Please Vote !!
Posted on May 13, 2010
Old timer: Intermatic EJ500 & ST01C timers have a battery. Battery operates the clock motor. Red wire is for 3-way circuit [a hallway with 2 switches is a 3-way circuit].
Utilitec timer, clock runs on 120Volt circuit instead of battery. So clock has to have power.
How to connect wires:
Black timer wire connects to hot wire from breaker box.
Red (or blue) timer wire goes to landscape lights.
White timer wire connects to white neutral wire [or if no neutral is available, connect to bare ground wire].
Green timer wire goes to bare ground wire.
How to find black hot wire and white neutral wire inside box: Disconnect and separate wires so you can test. Use ordinary tester. Power is on. There is only 1 black hot wire inside each electrical box. Test each black wire to bare ground until tester light comes on > that identifies the black hot wire. Next, test black hot wire to white wires until tester light comes on > that is the neutral wire. Exception: This test does not necessarily work with 3-way switches since they reverse each time switch is thrown.
Posted on Sep 21, 2010
Tips for a great answer:
Jun 19, 2011 | RTO Intermatic Digital 7 Day Wall Switch...
Apr 17, 2011 | Intermatic & Self-Adjusting Wall Switch...
Jan 25, 2011 | Leviton 6230M Decora Four Preset...
Dec 30, 2010 | Intermatic EI210 Electronic Auto Shutoff...
Oct 01, 2010 | Intermatic EI210 Electronic Auto Shutoff...
Jun 04, 2010 | Intermatic EI210 Electronic Auto Shutoff...
Mar 06, 2010 | Intermatic EI600WC - In-Wall Decorator...
Sep 03, 2017 | Intermatic EI210 Electronic Auto Shutoff...
Nov 12, 2008 | Intermatic EI210 Electronic Auto Shutoff...
726 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: