Question about Honeywell HE260A1010 Whole House Humidifier Humidifier
If you chose to install this with an auxilary transformer. Turn the main power off to the furnace. Mount the transformer on the handi box to the furnace or inside the furnace cabinet. Wire the primary wires from the transformer to the main power coming into the furnace. Connect black to black and white to white. Wire the secondary side of the transformer in "series" with a #50 relay, the humidistat, the solenoid valve and back to the transformer. Determine which wire powers the blower motor for the heating speed. Clamp the #50 relay to the wire.
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 20, 2011 | Honeywell HE360A1027 Whole House...
Jan 24, 2011 | Honeywell HE220A1019 Whole House...
Dec 28, 2009 | Aprilaire 600 Humidifier
Dec 11, 2009 | Aprilaire 550 Humidifier
Nov 18, 2009 | Honeywell HE360A1027 Whole House...
Jan 19, 2009 | Honeywell HE260A1010 Whole House...
Nov 25, 2008 | Honeywell HE260A1010 Whole House...
Dec 24, 2007 | Aprilaire 700 Humidifier
Jan 28, 2007 | Honeywell HE360A1027 Whole House...
542 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: