Question about Goodman Heating & Cooling
Before it even stats it will repeatedly ignite at 30 second intervals for about 12 times before starting.Then the heater will start up and after about 1 minute will turn off again It will repeat this process until the temperature level of the thermostat has been reached. After the thermostat level has been reached it will blow cold air though the ducts.
I need more info!
Have you checked the diagnostic indicator?
Some possibilities are....
If the buner lights than rapidly goes out....You have a dirty flame sensor..... Remove the sensor with a 1/4" nutdriver. This sensor is located under the burners. It has "ONE" wire hooked to it. unplug the wire. pull ou the screw. Carefully remove the sensor. Clean it with a small piece of sandpaper. reintall. This should give you heat.
Pressure switch.....If the burner does not light. It can be a variety of problems. Check your flue pipe for obstructions.
Heat anticipator in the t/stat
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 13, 2012 | 2000 Chevrolet Malibu
Apr 15, 2011 | Heating & Cooling
Feb 23, 2011 | 1997 Audi A4
Mar 09, 2010 | Dryers
Mar 08, 2010 | 2000 Ford Focus
Jan 09, 2010 | Honeywell Programmable Thermostat Heater
Jan 05, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 02, 2009 | Goodman GMS90703BXA Heater
Aug 10, 2008 | 2001 Dodge Ram 2500 Truck
116 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: