Question about Hayward Heatpro 100,000 Digi. Thermostat Heat Pump
Hayward digital heatpump purchased new 2 years ago, has white chalky build-up on outside coils (when not in use). When i tried to heat spa, I noticed icy frost forming all around unit ( &inside on copper), which caused unit to stop working properly. I sprayed the coils with garden hose water to melt, which caused normal operation to resume. Is there any thing I can do, besides service call?
Well Its a little complicated and unless you understand the heat pump /refrigeration cycle and the need for defrost and how the defrost is limited and initiated, well Id say yep...you need a pro.
About the only thing I can suggest you check is the initiate termination thermostat (assuming your Heat pump works with one of these). It will be identified by 2 wires going to it and it will be clamped on the line (Not brazed on or screwed on). Now there will also be a reversing valve which has 4 tubes going to it and 2 wires. and it could have high, low, pressure switches that have 2 wires. This thermostat is usually mounted 1/3 to 2/3 way down on the coil and is suppose to be mounted on the "U - Bend" of the out door coil tubing. It usually resembles a pancake and will have a wire or metal clip that holds it securely on the coil U bend. Make sure it hasn't fallen off or come loose. This can cause your heat pump to miss its required defrost.
You can try this also. Some defrost timer boards have a set of "test pins" you put them together with a screwdriver or a piece of wire for a few seconds to initiate a defrost. It defeats the time logic in the board It should go on into defrost and stay in until the coil is cleared of frost and or about 10 minutes which ever comes first. If it comes out right away it may be the termination switch I talked about above. It could also be the board. To check out the thermostat locate the 2 wires going to it from the board. pull them off the board and retry it. Sill goes right out of defrost then jumper the 2 wires together and try it again. If it still comes out this time it most likely the board. If it stays in defrost either time when removing the wires or jumping the wires its the thermostat.
Hope this helps you. If so please rate me as high as you can. Thank you for using fixya and good luck.
Hope this helps you
Posted on Mar 25, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Heating & Cooling
Apr 28, 2011 | Danby DDR607EE Dehumidifier
Sep 17, 2010 | Whirlpool Refrigerators
Dec 13, 2009 | Heating & Cooling
Dec 06, 2009 | Ruud UAMB042 Air Conditioner
Nov 13, 2009 | Refrigerators
Sep 12, 2009 | Whirlpool ET4WSKXS Top Freezer...
Dec 20, 2007 | Ruud UAMB Air Conditioner
Oct 26, 2013 | Hayward Heatpro 100,000 Digi. Thermostat...
119 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: