Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
I HAVE A RHEEM HIGH EFFICIENT FURNACE-EXHAUST VENTS TO OUTSIDE WITH A BLOWER MOTOR, WHEN IT IS WINDY OUTSIDE THE BACKDRAFT CAUSES IT TO SHUT DOWN AND TRY AGAIN FOR THREE TIMES THAN I HAVE TO RESET. IS THERE ANYTHING THAT CAN BE DONE TO PREVENT BACKDRAFT IN THIS UNIT?
Build some kind of barrier outside so the wind doesn't hit the vent. A piece of plywood before it or a big box around the vent. There is a pressure switch that the wind is messing with. It is a safety and necessary for the furnace to run properly.
Posted on Mar 25, 2009
It's the pressure switch on the unit. Make sure that the pressure switch doesn't have debris in it that keeps it from operating smoothly. Take the tubing off from the inducer side and breath in and blow out lightly while listening for a clicking noise. If that doesn't work then I would recommend replacing it. That should solve the issue.
Posted on Mar 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 25, 2016 | Rheem Water Heaters
Jan 09, 2015 | Emerson Lennox Ducane Armstrong Furnace...
Sep 20, 2014 | Heating & Cooling
Oct 26, 2013 | Gibson KG7TC060D24B 60,000 BTU 95.1% Gas...
Nov 16, 2012 | Rheem Prestige 14 Series 2.0 ton 14 SEER...
Oct 20, 2010 | Heating & Cooling
Jan 14, 2010 | Goodman GMS90703BXA Heater
Nov 01, 2009 | Fasco Bradford White Hot Water Heater...
Jan 26, 2009 | Goodman GMS90703BXA Heater
May 15, 2014 | Coleman Propane Forced Air Heater...
375 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: