Question about Honeywell HCM530 Humidifier
I have a Skuttle Drum Humidifier, Model 190, that operates by a humidistat. There is noise coming from inside the motor cover. It constantly wines when the humidifier is on.
SOURCE: Installation problem
I WOULD CHECK TO SEE IF YOU HAVE ENOUGH V/A OUT-PUT ON TRANSFORMER. I DONT KNOW IF YOURS CAME WITH ITS OWN TRANSFORMER. IF IT DIDNT YOU SHOULD HAVE A MINIMUM OF A 40 V/A RATING STAMPED OR PRINTED ON THE EXISTING TRANSFORMER. IF THE TRANSFORMER IS EXTREAMLY HOT ... YOU MAY NEED A 75 V/A TRANSFORMER WITH THE SAME VOLTAGES. INCREASING THE V/A CANNOT DAMMAGE ANYTHING IT JUST GIVES YOU MORE POWER WHEN EXCESIVE CONTROLS AND WIRING ARE ADDED TO A HVAC LOW-VOLAGE (24v) CIRCUIT. IF YOU LIKE YOU CAN CALL ME AT 727-363-7071. I AM A RETIRED HVAC&R CONTRACTOR WITH 45 YEARS EXPERIENCE. I HATE THE NEW SENSORS THEY HAVE TO ACTIVATE THESE NEW HUMIDIFIERS. I USE TO WIRE THE HUMIDIFIER TRANSFORMER (SUPPLIED WITH HUMIDIFIER) TO THE LINE (110V) SIDE TO THE LOW SPEED ON YOUR BLOWER MOTOR. THAT WAY THE ONLY THING THAT INTERUPTS THE CICUIT IS THE HUMIDISTAT. YOU NEVER WANT THE HUMIDIFIER TO RUN IF YOUR SYSTEM IS NOT "CALLING FOR HEAT". NEVER TRY TO ENERGIZE THE WATER SOLENOID THROUGH YOUR HEAT WIRE(USUALLY SMALL THE WHITE WIRE) FROM THE THERMOSTAT. THIS WILL RESULT IN BURNING YOUR HEAT ANTICIPATOR OUT ON THE T-STAT.
Posted on Apr 28, 2007
Maybe I can help. this is 24v so it doestn't matter which wire goes where so here goes. 2 wires from humidistat go to furnace, split one of the wires(not both) so they reach the yellow wires on the humidifier. with marettsconnect one of the split wires to one of the yellow wires. do the same to the other split wire and yellow wire. what you should get is one wire from humidistat to furnace then one wire from humidifier to humidistat and one from humidifier to furnace. hope this helps
Posted on Feb 04, 2009
if it works in the test mode then it should be okay but you can get a humidity gauge from radio shack and set in the house to see how high or low its is. the humidifier is only going to give a max of 45% humidity
Posted on Dec 31, 2009
Tips for a great answer:
Jan 26, 2015 | Honeywell HE120 Humidifier
Oct 09, 2013 | Aprilaire 700 Humidifier
Feb 20, 2011 | Honeywell HE360A1027 Whole House...
Feb 13, 2011 | Skuttle 190 Humidifier
Jan 19, 2011 | Carrier SBP Humidifier
Jan 18, 2011 | Aprilaire Humidifiers
Jan 31, 2009 | Honeywell HE360A1027 Whole House...
Jan 09, 2009 | Honeywell Power Humidifier: Furnace...
Jan 06, 2009 | Sunpentown 1500W Heater Fan Humidifier...
89 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: