Question about APC Silcon UPS System
Can you please give me the bypass procedure for an SL20KHB2 20KVA UPS.
First Press the user menu button
then scroll up or down till you reach on put UPS on bypass? Press C to change to YES if the default is already YES just press the # button then the UPS will go on bypass mode.
Go to UPS bypass panel and turn the bypass switch to (1) ON and Switch the Output on the bypass panel to off. Now you're already on a bypass mode.
if you have any query please drop me an email.
Posted on Aug 14, 2009
Tips for a great answer:
Nov 25, 2014 | Liebert (GXT2-10000T230) (GXT2-10000T230)...
Mar 25, 2014 | MGE UPS Galaxy 3000 UPS System
Jan 15, 2014 | APC Symmetra PX (SYCF80KF) UPS System
Nov 21, 2013 | APC Smart-UPS VT 20kVA (SUVT20KF3B4S) UPS...
Feb 18, 2013 | Eaton Powerware 9355 UPS System
Feb 04, 2011 | MGE UPS Galaxy 3000 UPS System
Nov 03, 2010 | APC Symmetra Tune-UPS technical support -...
Oct 14, 2009 | Eaton PW9390 UPS System
Jul 19, 2009 | APC Smart-UPS 1000VA UPS System
372 people viewed this question
Usually answered in minutes!