Question about Aprilaire 1120 Humidifier
When furnace stops and Aprilaire is off water keeps coming
Disconnect the two yellow wires. The water should stop. If it does you have a bad (or miswired) humidistat. If the water does not stop the solenoid valve is bad. These valves are known to be expensive. You might want to consider replacing the whole unit.
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 13, 2013 | Aprilaire Humidifiers
Dec 01, 2012 | Humidifiers
Feb 05, 2010 | Aprilaire 700 Humidifier
Jan 31, 2010 | Aprilaire 550 Humidifier
Jan 08, 2010 | Aprilaire 600 Humidifier
Dec 11, 2009 | Aprilaire 700 Humidifier
Feb 18, 2007 | Aprilaire 700 Humidifier
Apr 01, 2009 | Aprilaire 1120 Humidifier
496 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: