Question about Goodman Heating & Cooling
Goodman GSZ130241A / ARUF182416
The Goodman unit now sounds like this during the defrost cycle:
The unit ran reasonably quiet for several months (installed Nov 2008) with just a very short clang at start.
New HVAC tech had a quick look at unit and is returning in a day or so when he has more time to remove refrigerant as a start in diagnosing problem.
Here is what he found:
40 F outdoor ambient - 73 F indoor
Hi PR 410 / Lo PR 96 Discharge temp 158
Air handler tested w/ actual measured voltage/current:
Hi speed: 19 F temp rise = 947 CFM
Mid speed: 21 F temp rise = 856 CFM
Unit was originally charged by weight (6 oz added) by different tech who said unit was installed correctly. They state that this is ''normal'' noise.
Could the factory overcharge (if that is the case) or other malfunction creating high pressures cause permanent damage to scroll resulting in this noise?
The unit heated (and defrosted) very good and the original noise levels were better than a neighbors unit. I was very pleased with it until it started making this noise.
Overcharged temperature split times cfm gives you btu's did he check static pressure .50 or less
Posted on Feb 19, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 27, 2015 | Goodman Heating & Cooling
Aug 27, 2013 | Frigidaire FRS3R5EMB Side by Side...
Sep 23, 2011 | Hotpoint Refrigerators
Apr 08, 2010 | Whirlpool Refrigerators
Feb 01, 2018 | LG LFX23961ST Stainless Steel Bottom...
Mar 04, 2009 | Goodman Heating & Cooling
Jan 17, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 04, 2009 | LG LD50EL Dehumidifier
Dec 06, 2008 | Goodman CLQ36AR49 Air Conditioner
Nov 22, 2008 | Goodman CLQ36AR49 Air Conditioner
317 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: