Question about Sharp CV-P09FX Air Conditioner
Weekend cabin - recently had an ice storm. I noticed that the heat pump fan is not running when the house heat and blower is. Fear I am running on straight electric heat (expensive). is the heat pump suppose to run the fan when heating? Outside temp was 35 f with inside at 68 f.
The outside fan should be running except when the Heatpump goes in to defrost mode. Then the fan stops with the compressor running and it switches the reversing valve to heat up the outdoor coil. That should last about 5 min and you may see steam come off of the outdoor coil. That's normal.
Is the compressor running? It's possible that it's stuck in defrost or the fan simply died. I hope this helps.
Posted on Feb 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 26, 2016 | Heating & Cooling
Mar 16, 2015 | Amana PTH153B50AJ Heat Pump Air...
Mar 06, 2015 | American Standard 5000 Heat Pump Unit
Nov 01, 2014 | Heating & Cooling
Nov 25, 2013 | LG LAN186HV / LAU186HV 18,000 BTU 15 SEER...
Oct 29, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Jan 24, 2011 | Heating & Cooling
Feb 05, 2010 | Goodman Heating & Cooling
Jan 12, 2010 | Carrier 38CKC042 Air Conditioner
565 people viewed this question
Usually answered in minutes!