Question about Heating & Cooling
I have a 2.5hp split system fujita and when it was fitted it worked perfectly, however when I went to use it again the system wouldn't work. thought it was out of gas but found out it worked if you activated it manually. Rang the sevice spare parts mob and they quoated $180 for the board in it. there started the problems because there is 2 boards in one for the remote which is the 1 that is blowen which they didn't know about and the main board ($180). Still waiting for the spare parts mob to get back to me!!!!!! Help
My Fujita remote stopped working, you would unplug the unit & turn it back on, the system would go into a test of the airflow lever (opens & shuts), remote would not turn on unit, found that on back of receiver board where 3 wire plug connection is, solder joint had shorted across from r to - . scratched this away with screwdriver carefully & all ok.
to get to board you remove 3 screws in filter cover & 3 plastic covers with 3 screws below air flow lever, just lift up cover enough to remove 1 screw holding remote receiver board in.
Posted on Mar 09, 2013
I am pretty sure you would only need to buy the remote board, but before you do, you could try to resolder all the joints on this board. It is a small board with a couple of LED and remote sensor. Then make sure it is plugged in well, and give it a try.
Posted on Mar 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2016 | RC Toys
Jan 09, 2016 | Filter Heating & Cooling
Dec 24, 2015 | Heating & Cooling
Dec 14, 2013 | Heating & Cooling
Sep 27, 2013 | Heating & Cooling
Jan 31, 2011 | Heating & Cooling
Jan 06, 2011 | Heating & Cooling
Feb 03, 2008 | Heating & Cooling
Nov 20, 2007 | Heating & Cooling
765 people viewed this question
Usually answered in minutes!