Question about Aprilaire 600 Humidifier
Model 560 worked last year. I noticed there was no codensation after I cranked up the humistat all the way. Opened the panel and the entire unit is bone dry. Cleaned filter, nozzle, feed tube, orifice, etc...
I onlu want to change the solenoid if I have to. Can I run Volt/Ohm testing to see if the solenoid is working?
Yes, just check to see if you have 24 volts going into the solenoid. If you do and it is not opening its probably bad. Since you verified the water lines, filter, orifice and saddle valves are not obstructed. Change the solenoid valve. When you price the part. (it's not cheap) consider paying about 30% more and just change the whole unit.
Posted on Mar 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 29, 2011 | Aprilaire 550 Humidifier
Nov 16, 2010 | Aprilaire 600 Humidifier
Oct 12, 2010 | Aprilaire 550 Humidifier
Jan 06, 2010 | Aprilaire 550 Humidifier
Dec 31, 2009 | Aprilaire 558 Humidifier
Dec 20, 2009 | Aprilaire 550 Humidifier
Aug 19, 2009 | Aprilaire Humidifiers
Feb 07, 2009 | Aprilaire Humidifiers
Dec 25, 2008 | Aprilaire 700 Humidifier
218 people viewed this question
Usually answered in minutes!