Question about Mr. Heater MHU45LP
Heater is flashing 3 times indicating pressure switch failed closed before CAB is energized wondering what this means.Is this gas line pressure
Just purchase the 75k btu natural gas Mr. Heater. It would light and run until it reached the setting on the thermostat, then wouldn't relight and had the code 3. I found when assembled from the factory, the service door was install unside down. This heater can be installed right side up or inverted. Once I turned the access door 180, the heater works like a swiss watch. This heater works perfect to heat my 750 square garage. Very satisfied.
Posted on Apr 01, 2012
The pressure switch to which you are referring is the switch connected to the suction side of your induced draft fan. This pressure switch will have a hose connected between the switch and the induced draft fan. Please let me know if you need any more assistance.
Posted on Feb 17, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 17, 2015 | Water Water Heaters
Jan 23, 2008 | Goodman GMS90703BXA Heater
Mar 02, 2014 | Mr. Heater MHU45LP
Aug 03, 2013 | Jandy Laars LX Pool Heater / 400,000 BTU /...
Jan 02, 2011 | Goodman GMS90703BXA Heater
Dec 03, 2010 | Goodman GMS80903BNA Heater
Jan 16, 2010 | Mr. Heater MHU45LP
Jan 10, 2010 | Goodman GMS90703BXA Heater
Jan 02, 2010 | Goodman GMS90703BXA Heater
Dec 12, 2009 | Heating & Cooling
1,071 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: