Question about Carrier 38BRC060 Air Conditioner
I'm not a fan of zoning but it sounds like they don't have the ducting done correctly. There has to be bleeder trunks installed in the unit because your are taking a unit that is designed to cool or heat a particular square footage and make it cool or heat a smaller area. This makes the unit way too big for the job you are asking it to do. If the ducting is improper, you are going to have issues like this. A lot of contractors will not admit that the ducting isn't correct due to the cost to correct it. I personally think (my opinion) that 4 zones are a little excessive. Sounds like you really need 2 units. It's hard to tell from my point of view since I'm not there to actually see what is going on. I would have a couple of different contractors come out and give you an estimate to fix the issue and then tell the installer to come and fix what they say is wrong.
Posted on Mar 16, 2009
Tips for a great answer:
Jul 27, 2014 | Honeywell Motorized Small Rectangular Hvac...
Sep 04, 2013 | Air Conditioners
Sep 25, 2010 | Air Conditioners
Nov 14, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 12, 2009 | Carrier 38CKC042 Air Conditioner
Aug 03, 2009 | Carrier 38CKC060 Air Conditioner
Jul 01, 2009 | Carrier 38CKC042 Air Conditioner
Feb 18, 2009 | Carrier 38CKC060 Air Conditioner
Feb 02, 2009 | Air Conditioners
Jan 22, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
May 13, 2012 | Carrier 38BRC060 Air Conditioner
131 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: