Question about Honeywell Programmable Thermostat Heater
Got honeywell cm 61ng wirerless remote,green light on relay box on bottom light flashin red,remote will not turn boiler on or off,we have to keep goin in loft to turn heatin on and off.
What's happened here is the cm61 ng and the reciver box have lost there connection you will have to "rebind" them then it will be fine -
THE BINDING OPERATION DESCRIBED BELOW IS REQUIRED IF:
· Any of the system components (room unit or relay box) are replaced
· HC60NG has incorrect or no binding data stored (e.g. when pre-bound system pack components have been mismatched)
· Interference with the RF signal has caused a communication failure
During the binding procedure keep approximately 1m distance between the room unit and the HC60NG
1 Turn off mains supply to HC60NG for 10 seconds. Re-connect supply.
2 Press and hold the HC60NG push button for 15 seconds to reset previously stored data. The red LED will start to flash at 0.1 s on/0.9 s off. Release the push button.
3 Press and hold the HC60NG push button for 5 seconds to enter the binding mode. Red LED flashing at 0.5 s on/0.5 off confirms the binding mode has been entered.
4 Move the CM67NG slider to the OFF position (CM61 push the OFF button) and press the TEMP , TEMP and PROG 1 buttons together. The CM61/67NG will display InSt.
5 Press the i button to send the binding signal. The red LED is switched off on the receiver box to confirm the successful binding operation. If the red light still flashes push the repeat steps 1-3 and press the the i button until binding is successful.
hope this is helpful
Posted on Feb 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 10, 2012 | Honeywell Aube by TI0323WU 7Day...
Sep 13, 2008 | Honeywell Heating & Cooling
Nov 07, 2011 | Honeywell Programmable Thermostat Heater
Jan 29, 2011 | Honeywell Programmable Thermostat Heater
Sep 25, 2010 | Honeywell Programmable Thermostat Heater
Feb 14, 2010 | Honeywell Programmable Thermostat Heater
Oct 31, 2009 | Honeywell Programmable Thermostat Heater
May 03, 2009 | Video Game Consoles & Games
Feb 22, 2009 | Bosch Logixx WFT 2806 Front Load...
Nov 14, 2008 | Honeywell Programmable Thermostat Heater
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
Apr 27, 2016 | Honeywell Programmable Thermostat Heater
2,789 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: