Question about Ruud UBHC Air Conditioner
I have shut everything down.
Turned up thermostat
Turned on gas
Turned on power
Induced draft motor starts
Igniter warms up (glows red)
Main burner lights
Main burner remains powered and lit
Indoor blower motor FAILS to start
System SHUTS DOWN
What is causing the blower motor not to start? It suggests to clean the flame sensor unit with steel wool in my manual but doesn't tell me where it is.
Cleaning the flame sensor has nothing to do with blower motor not turning on. You either one of the following problems 1 bad cap for motor. 2 bad motor. 3 bad limit on blower housing or 4 a bad board. You will need a volt meter to check for these problems. Try seeing if the fans runs with unit of and fan switch turned to on. Also does motor hummmm. Is motor cage free ( can check by manually turning) If motor doesnt humm and the cage is free wheeling then you will need to find out if you have power going to the motor. If you find out that you do then you will need to change blower motor. If you do not have power then you will need to check limit with continuity tester on volt meter. If that checks fine only 1 thing can be wrong and that is the board.
Posted on Feb 16, 2009
Tips for a great answer:
Nov 03, 2013 | Ruud Gas Furnace - Excellent Condition -...
Feb 19, 2013 | Air Conditioners
Jan 06, 2012 | Air Conditioners
Jan 06, 2011 | Goodman Air Conditioners
Nov 28, 2010 | Ruud UBHC Air Conditioner
Nov 17, 2010 | Air Conditioners
May 13, 2010 | Ruud UBHC Air Conditioner
Mar 22, 2010 | Ruud UBHC Air Conditioner
Nov 28, 2009 | Air Conditioners
249 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: