Question about Hunter Fan Company 5/1/1 Programmable Thermostat
Make sure you do not have a jumper between the red and the white. Also make sure the wire is not hanging out from behind the screws. If the heat stayes on no matter what you do. The red wire has to be touching the white somewhere.
The red is your 24v supply to the thermostat
The white is what sends the 24v to the heat side of unit.
Just a thought. If the thermostat has a O/B pin or switch on the back. Make sure it's on O. It should only be ob B if it's a Trane, American Standard or Payne.
Posted on Oct 16, 2009
not all digital thermostats are compatible with the manufacturers circuit control boards in the furnace. Hunter has had this problem several years ago. Other than that you may have miss wired the unit. usually the furnace is used as backup heat (during defrost) or emergency heat if your heat pump konks out. Are you switching to emergency heat for a furnace call?
Posted on Nov 24, 2009
Is this a heat pump? Look in the thermostat. You should have something like the following.
Red wire to R terminal
Green wire to G terminal
Yellow wire to Y terminal
White wire to W or W1
Blue or Orange wire to the O or B terminal
Brown wire to C terminal.
Let me know what you have in the thermostat. The wire colors are not always the same.
Posted on May 23, 2010
Tips for a great answer:
Dec 23, 2010 | Hunter Fan Company 5/1/1 Programmable...
Dec 06, 2009 | Hunter Fan Company 5/1/1 Programmable...
Nov 24, 2009 | Hunter Fan Company 5/1/1 Programmable...
Jul 11, 2009 | Hunter Fan Company 5/1/1 Programmable...
Dec 14, 2008 | Hunter Fan Company 5/1/1 Programmable...
Feb 07, 2008 | Hunter Fan Company 5/1/1 Programmable...
Nov 14, 2007 | Hunter Fan Company 5/1/1 Programmable...
127 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: