Question about Delfield 'New 6000XL 6051 Side by Side Refrigerator
I am the second mechanic on this Unit. 1st mechanic changed out compressor and TX valve. I then changed another compressor 2 years later and removed tx valve installed cap tube (unit has no receiver), now unit will not go below 47 degrees. What is the problem?
I had a similar situation, unit cooling at about 45 deg, pressures were 10 low, 250 high.
Replaced capillary tubing, now unit cools at or below 38 deg, pressures 30 low, 225 high
Posted on Jul 24, 2009
How was this unit originally equipped? TXV? Use only a TXV OF CORRECT size. In refrigeration if you have a 6000btu rating you do not use a 1/2 ton valve you use a 1/4 ton (3000btuh) at most and would need consulting with an engineer to arrive at the correct valve.
SO was the TXV the other fellow replaced an OEM valve? If not this may be the problem as most TXV's off the shelf are designed for walk-in refrigeration Not Reach ins. An OEM valve may be the trouble here.
Now not to stress the TXV but also the compressor (what was the original model?) Make sure it is designed for the particular heat range and size for this application. As you probably know 1 size compressor designs for AC will not be OK on Refrigeration at same BTU rating.
Call Del field and verify what they are using or recommending for this unit. model and Seal no required and the existing model and SN.
Also to my knowledge a receiver is not required and in fact will only add to your trouble. Receivers are for changes (wide differences) in condensing temperature and pressure. Never saw an application for one with a condenser designed from factory for indoor use with either type of expansion device.
If you need Del fileds number email me at email@example.com and in th subject line enter delfield?.
Posted on Apr 14, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 25, 2011 | Delfield 406 / 406-CA Refrigerator
Oct 26, 2010 | Delfield 'New 6000XL 6051 Side by Side...
Oct 11, 2010 | Delfield 406 / 406-CA Refrigerator
Jun 23, 2009 | Traulsen Commercial 2 Door Cooler /...
Dec 19, 2008 | Delfield 'New 6000XL 6051 Side by Side...
Nov 30, 2008 | Whirlpool 25.6 cu. ft. Side-by-Side...
Jul 14, 2008 | Delfield (F18WC60) Commercial Refrigerator
Aug 07, 2007 | Delfield 032-F2FH ColdPro Solid Door Reach...
Oct 23, 2015 | Delfield 'New 6000XL 6051 Side by Side...
Sep 03, 2010 | Delfield 'New 6000XL 6051 Side by Side...
218 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: