Question about Goodman GMS90703BXA Heater
I have a goodman heater and it is blinking six times. it read that six blink means open rollout. the roll is good and i still replaced it and the furnace still blinks six times. what can be the problem? the fan works but nofire
Did the furnace kick in at all after you replaced the rollout? if it did run then check the filter make sure its clean, or even leave it out for a bit. if it didnt run after you replace the roll out then switch the breaker off then wait ten seconds then turn back on this will reset the ciruit board and it should try to cycle. next thing you can try is jumper the roll out switch DO NOT LEAVE IT JUMPERED, its just to double check that its not the roll out, if it works jumpered replace the roll out again and try that. if none of that works take out the crews on the ciruit board and check the back. sometime when a ciruit board fails there will be a burn mark somewhere on the back, if there is replace it.
Posted on Feb 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 17, 2014 | Goodman Manufacturing Goodman DSXC180601...
Jan 27, 2014 | Goodman GMS90703BXA Heater
Nov 24, 2012 | Goodman GMS90703BXA Heater
Dec 04, 2010 | Goodman GDS80904BNA Open Flame Heater
Oct 19, 2010 | Goodman Heating & Cooling
May 28, 2010 | Rheem 266K to 399K BTU Swimming Pool...
Dec 21, 2009 | Goodman GMS90703BXA Heater
Oct 06, 2009 | Goodman GMS90703BXA Heater
Mar 03, 2009 | Goodman GMS90703BXA Heater
152 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: