Question about Powerware Best Power Unity/I UPS System
The UPS is question is a Best Unity/I single phase UT3K. New batteries have been placed into this unit, they are maintaining correct voltage, and when the battery load test is run they pass. From turning the unit on after around 7 hours the "Check battery" warning alarm A-04 is displayed and cannot be cleared. If this unit is turned off and on again the alarm does not reappear for another 7 hours or so and the unit will also pass the battery test. I don't think there is anything wrong with this unit, but I don't like to leave it running with the alarm. Perhaps I need to edit one or more of the many many internal settings?
1) By the way, batteries are really new (or "China new")? ;)
If they really new then maybe not start-formed. In this case after little time they will get steady (end of problem). If they are "China new" - it worse, their real capacity usually less then 75% from declared.
2) Try to check batteries connectors, wires and their eyelets. If there is weak contact - charging will be wrong (low current)...
3) Check small orange (voltage sence) connector...
4) Look, what happened with P-62, P-63, P-74 ang P-75 settings? maybe there something is wrong...
Maybe, it will be helpfull?
P.S. Please, excuse my weak english.
Posted on Apr 14, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 12, 2011 | APC SMARTUPS RT 15KVA RM 230V...
Dec 12, 2010 | Powerware Best Power Unity/I Three-Phase...
Oct 29, 2010 | Powerware Best Power Unity/I Three-Phase...
Sep 15, 2010 | Powerware Best Power Unity/I Single-Phase...
Jul 09, 2010 | Powerware Best Power Unity/I Single-Phase...
Nov 05, 2009 | Zenith ZTG Nema-3R, 400 Amps Three Phase,...
Feb 11, 2009 | Powerware Series 9 9150 UPS System
184 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: