Question about Intertherm P3RA-048K Air Conditioner
I have a intertherm furnace model #m1mb77ab its alittle over 2 years old sometimes the flame will not ignite it the red light flashes 1 time meaning limit switch is open sometimes it flashes 2 times meaning pressure switch is open were are these located
How often do you replace your filter?
On the limit switch that protects your unit when it gets to hot the number one reason is dirty filter.
The pressure switch is located in the upper side of cabinet has a rubber hose connected to it. They very rarely go out though. So find your vent fan the first fan that comes on and follow the rubber hose to the switch.
Posted on Feb 11, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 29, 2015 | Intertherm 56000 Btu Gas Furnace
Nov 20, 2014 | Intertherm Heating & Cooling
Oct 20, 2011 | Intertherm P3RA-048K Air Conditioner
Sep 15, 2011 | Heating & Cooling
Dec 05, 2009 | Dayton (3E407) Heater
Apr 05, 2009 | Intertherm P3RA-048K Air Conditioner
Jan 18, 2009 | Intertherm P3RA-048K Air Conditioner
Dec 14, 2008 | Cross Furnace Draft Inducer Blower 115...
Dec 05, 2008 | Heating & Cooling
355 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: