Question about Gardner Bender #GSW-SK Door Switch
Just installed a Gardner Bender SPST Switch Kit (GSW-SK) for my coat closet so the light comes on when the door is opened. Went to reset the breaker but it won't. Clearly something is wrong. I have two cables entering the metal switch box, one from the source, the other to the light. The GB switch itself has only two wires, which I connected one to the other two whites, the other to the other two blacks. I connected the two ground wires to the back of the metal box with the screw provided. Does anyone see anything wrong with this hook up? I was surprised the switch didn't come with a ground wire... Thanks.
Leave the original whites connected together, connect the new switch in series with the two black wires (one black to the top of the switch, the other to the bottom),
p.s. the switch is grounded through the mounting strap
Posted on Feb 08, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 17, 2011 | Gardner Bender #GSW-SK Door Switch
Feb 05, 2011 | Gardner Bender #GSW-SK Door Switch
Jan 08, 2011 | Gardner Bender #GSW-SK Door Switch
Sep 12, 2010 | Gardner Bender #GSW-SK Door Switch
Feb 11, 2010 | Gardner Bender #GSW-SK Door Switch
Oct 16, 2009 | Gardner Bender #GSW-SK Door Switch
Sep 29, 2009 | Gardner Bender #GSW-SK Door Switch
Jun 15, 2009 | Gardner Bender #GSW-SK Door Switch
Jun 11, 2017 | Gardner Bender #GSW-SK Door Switch
388 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: