Question about Sta Rite STA-RITE SENSOR,FLUE TEMP - 42002-0024S
What is the value of resistance? of stack Flue Sensor Part #42002-0024S of heater Sta Rite SR 400LP. Thanks
Are you getting E05 error? I can't give you the value, but it is possible to bypass the switch. Unhook the sensor connection wires and jump them together. Hold off switch until a code comes up - press down arrow once to change last value from 1 to 0, press off again and do the same thing with the next value and change it from 1 to 0, press off again. Unit should work now until you get a new sensor and then just change the settings back.
Posted on Mar 17, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 27, 2014 | Sta Rite STA-RITE SENSOR,FLUE TEMP -...
Aug 23, 2012 | Sta Rite STA-RITE SENSOR,FLUE TEMP -...
Apr 30, 2011 | Sta Rite Sr400na Max E Therm Pool & Spa...
Jan 21, 2010 | Sta Rite Sta-Rite Max-E-Therm High...
Jun 14, 2009 | Sta Rite Sta-Rite Max-E-Therm High...
Jan 22, 2018 | Pool & Spa
1,706 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: