Question about Sta Rite STA-RITE SENSOR,FLUE TEMP - 42002-0024S
What is the value of resistance? of stack Flue Sensor Part #42002-0024S of heater Sta Rite SR 400LP. Thanks
3.5 to 4K If you want to bypass the sensor just jump a 1 dollar resistor in between the two wires. If you want to put another sensor just use a standard gas heater flute sensor(2dollars) and put in line with the resistor
Posted on Nov 26, 2009
Are you getting E05 error? I can't give you the value, but it is possible to bypass the switch. Unhook the sensor connection wires and jump them together. Hold off switch until a code comes up - press down arrow once to change last value from 1 to 0, press off again and do the same thing with the next value and change it from 1 to 0, press off again. Unit should work now until you get a new sensor and then just change the settings back.
Posted on Mar 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 27, 2014 | Sta Rite STA-RITE SENSOR,FLUE TEMP -...
May 24, 2014 | Sta Rite STA-RITE SENSOR,FLUE TEMP -...
Apr 30, 2011 | Sta Rite Sr400na Max E Therm Pool & Spa...
Jun 19, 2010 | Sta Rite Sta-Rite Max-E-Therm High...
Jan 21, 2010 | Sta Rite Sta-Rite Max-E-Therm High...
Jun 14, 2009 | Sta Rite Sta-Rite Max-E-Therm High...
1,604 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: