Question about Carrier Heating & Cooling
Have Carrier 58GP075-3 furnace
The burners come on and run tell the blower kicks on, at the exact same time blower comes on burners go off.
Blower runs for about a minute, then at the exact same time blower goes off burners come on again, keeps repeating this cycle.
MY FURNACE WOULD RUN FOR ABOUT TWO MINUTES , THEN THE BURNER WOULD GO OUT BUT THE BLOWER WOULD CONTINUE TO RUN , LONG ENOUGH TO COOL THE FAN LIMIT SWITCH DOWN , THEN IT WOULD START THE PROCESS ALL OVER. WHAT FIXED MY PROBLEM WAS THE SECONDARY HEAT EXCHANGER THAT IS LOCATED JUST ABOVE MY BLOWER MOTOR WAS PLUGGED WITH DIRT , WHICH RESTRICTED THE AIR FLOW , CAUSING THE FAN LIMIT SWITCH TO REACH 200 DEGREES AND SHUT THE BURNER DOWN . YOU'LL HAVE TO TAKE THE BLOWER MOTOR OUT TO GET TO IT , BUT MY FURNACE IS RUNNING PERFECT NOW
Posted on Jan 11, 2010
Sounds like mine did
it was a realy switch
Posted on Feb 06, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2015 | Heating & Cooling
Oct 07, 2014 | Heating & Cooling
Sep 14, 2011 | Heating & Cooling
Feb 24, 2011 | Dayton Gas Furnace Heater
Oct 29, 2010 | Electric Circuit Breaker Kit for Furnace
Oct 22, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 06, 2008 | Carrier Heating & Cooling
Dec 17, 2007 | Heating & Cooling
1,119 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: