Question about Heating & Cooling
The "Aux HT" indicator went on, however the room temp will not go up.
I change the mode to "EHEAT", the fan on the outside unit stopped, "Aux HT" indicator is still on, however the room temp still not goes up. The air comes out of the vent is warm but not hot...
Any hint what's going on? Thanks a lot! The AUX HT Came on my thermostat, what is this, and should I be worried about it? Should I put it on EHeat instead for some reason? It is pretty cold outside (in the low 20's). My unit is not that old, is there a problem? Please help!!
You have a heat pump which removes heat from outside air when it is too cold out below 30* the unit can no longer produce heat and electric strip heaters kick in
Posted on Feb 06, 2009
The unit is probably to small for theare you are trying to heat.
When the Aux HT light came on that meant the heat pump could not keep up with the demand for heat. (Probably due to extreme cold, or undersized unit.)
If yu have heat, then at least one heat strip is operating. If you have multiple heatstrips, one or more could be malfuncioning.
Or it could simpy be to cold/to small fr your area and not able to keep up.
How many square foot are you trying to heat?
What is the outside temp?
What is the inside temp?
What size unit (BTU output) do you have?
Posted on Dec 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2015 | Emerson 1F89EZ-0251 Blue 2" Thermostat,...
Aug 18, 2014 | Heating & Cooling
Nov 25, 2013 | Heating & Cooling
Nov 08, 2013 | Honeywell TH3210D1004 PRO 3000...
Jan 04, 2010 | Honeywell Electronic Programmable...
Dec 11, 2009 | Goodman Heating & Cooling
Mar 15, 2009 | Heating & Cooling
Jan 23, 2009 | GE Zoneline AZ55H09D Air Conditioner
Dec 22, 2008 | Haier Energy Star ESA3183 Air Conditioner
Feb 21, 2017 | Heating & Cooling
490 people viewed this question
Usually answered in minutes!