I just had an Aprilaire 700 installed on my 90k hi eff furnace (new last year). I keep hearing a hi pitched whistle when the humidifier goes on. Trying to get the HVAC guy back - but he's busy installing and fixing furnaces - very cold this week.
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US. click here to Talk to a Repairman (only for users in the US for now) and get all the help you need. Goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Hello, seems like there is no way to turn on the humidifier. There would either need to be a new transformer installed, a current sensing relay, or a sail switch to activate the humidifier when the blower motor kicks on.
Install new water panels yearly. On the new panel make sure that the painted dot on the edge of the panel is on the top when you install it.
Always clean the distribution tray and the frame. Make sure the notch on the edge of the distribution tray faces away from the furnace. Make sure the humidifier was installed level. Keep the drain tube opening clear. Insure there is no blockages in the drain tube.
I called the service company that put in my new furnace (FAmily Heating and Cooling in Detroit, very highly recommend these people)
Anyway they sent out a second service tech who determined that I would be better off having the humidifier wired to go on whenever the furnace fan was running instead of using the humidifier signal from the circuit board on the furnace. After he changed the wiring the unit runs fine. It is pretty likely that the circuit board was bad also.
sounds like either the motor is off balance
or is going bad again
either way id be on the phone to the guy who did the rapair
more than likely the set screw on the sqiral cage came loose and now its vibrating
I have had the same problem , off and on, on my two 700 units for over 4 years. It is caused by water hammer which results when a water solenoid valve closes quickly under pressure. Refer to your owners manual or get a copy of it off the internet. Note the areas where they tell you to remove and clean the inline water strainer and the inline orifice restrictor. These are VERY small components and can clog up easily so they need to be cleaned per the manual. While cleaning them won't totally eliminate the problem it has helped mine with the noise. You really need to have a qualified person, like a plumber, install a small, water hammer arrestor in the inlet line. The trick is to be sure it ends up parallel to the water line flow and not perpendicular to it.... a common mistake. If you are not qualified to work on solenoids and piping, don't do it......it will end up costing you more to repair your mistakes. Good luck