Question about Heating & Cooling
Ever so often the exhaust fan comes on and then the burners ignite and burn for a minute or so and then go out. The exhaust fan continues to run sometimes about 4 minutes or longer then the indoor circulating fan comes on with heat. WHAT IS THE PROBLEM----goodman gaspack.
Posted on Mar 23, 2010
Then you need toi have them check the fan high limit that is mounted in the blower compartment. if it's closed then the blower fan and the conmbustion air fan will run together.
Posted on Feb 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 12, 2016 | Goodman Heating & Cooling
Nov 02, 2010 | Goodman Heating & Cooling
Jan 04, 2010 | Goodman Heating & Cooling
Feb 03, 2009 | Goodman GMS90703BXA Heater
Feb 03, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 29, 2009 | Heating & Cooling
Jan 28, 2009 | Goodman GMS90703BXA Heater
Jan 27, 2009 | Goodman CLQ36AR49 Air Conditioner
Oct 21, 2008 | Goodman CLQ36AR49 Air Conditioner
Sep 21, 2008 | Goodman Heating & Cooling
342 people viewed this question
Usually answered in minutes!