Question about ACCO Brands Water Heaters
Our Baxi Combi boiler pressure gauge is reading 0. It goes up to 0.5 if hot tap used but always on 0, how can we try and fix? Also which may be connected, a radiator upstairs is only heating up the bottom half. We've tried bleading it, but the air comes out, stops like none is left, and that is it. No water spurts out. Any help on this would be great!!
P.S The product is a Baxi Combi Bolier 24, but wasn't listed below.
The first thing you need to do is to put some more water into your heating system. This is usually done by allowing water from your (pressurised) domestic cold water supply to flow into the system: On older boilers, this is done with a connection (often made with a removable hose) on the pipework just outside the boiler. Newer boilers may have a built-in connection with some sort of removable link (sometimes looks like a plastic key).
Once you've got the boiler up to working pressure (typically about 1 bar - 15 psi), you should be able to bleed your upstairs radiator properly.
This may be all it takes, though the pressure excursions you're getting when you run the hot tap suggest there may be another problem. See what happens to the pressure as the boiler heats up and cools down. There really ought to be very little pressure difference between the two conditions. If you see significant changes, this usually means that the "pressure vessel" (or in hydraulic terms, system accumulaor) has lost its air charge.
The pressure vessel is a metal container inside the boiler, usually painted in red enamel. Somewhere near the top, you will find a schrader valve (like the one on a car tyre), and you can use this along with a tyre pump to replenish the air in the top of the vessel. This will reduce your pressure transients for a while, but you need to keep an eye on it. If the problem returns, you probably need to replace the pressure vessel (or clag another one into the plumbing alongside the boiler).
Posted on Feb 03, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 09, 2016 | Water Water Heaters
Jan 28, 2013 | Water Heaters
Oct 23, 2012 | Water Heaters
Jan 23, 2011 | Water Heaters
Oct 09, 2009 | Water Heaters
Mar 27, 2009 | Water Heaters
Mar 23, 2009 | Water Heaters
Oct 15, 2008 | Protech Systems FasNSeal FSWMKE4 4" Vent...
960 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: