Question about Heating & Cooling
Have a problem with my furnace, and I hope you can help me. I switch the tstat to call for heat, and the following is what I get ..... 1. The Combustion blower starts. 2. Then I hear a '' CLICK '' 3. There is a long quite moment. 4. The another '' CLICK. '' 5 Finally the main blower turns on, and all we have is cold blowing air. NO HEAT. I never see the Igniters glow, and I only smell a hint of gas. MAKE : LENNOX MODEL:G26Q3-75-1 S/N 5894L37210
Sounds like the ignitor is bad. there shoule be a 2 wire plug going to it. after the inducer motor starts, you can check the voltage at the 2 wire plug located under the burners. you can unpug it to check voltage or you can probe the back side of the plug with a volt meter. if you are getting 120v but it is not glowing, it is bad. you can also ohm it out while it is off.
Posted on Feb 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 05, 2017 | Heating & Cooling
Mar 21, 2017 | Coleman Heating & Cooling
Mar 21, 2017 | Honeywell Heating & Cooling
Oct 08, 2012 | Heating & Cooling
Apr 18, 2017 | Heating & Cooling
Feb 16, 2010 | Heating & Cooling
Dec 31, 2009 | Superior Lennox Blower Thermal Sensor -...
Jun 18, 2009 | Heating & Cooling
Jan 13, 2009 | Honeywell Electronic Programmable...
Mar 18, 2017 | Heating & Cooling
382 people viewed this question
Usually answered in minutes!