Question about Water Heaters
Gauge normally showsreading between 1-2 which i take to be correct. however when the heating was switched on today the gauge showed nearly 3. it started to drop after heating was switched off.
A couple of things , is your filling loop disconected ? , and are all your radiators blead from air, have you got a high point where the air can get stuck in system say pipes going into roof etc you may need to fit a air release valve in line at highest point to remove the air from system , your boiler should be around 1.5 bar running preasure average setting . if you are constanly filling with water you could be exceeding the pressure valve limet which releases pressure from system this could be faulty ?
Posted on Feb 05, 2009
Boiler fires for short time only then seems to switch off. we have tried over ride button but it only works for few seconds
Posted on Jan 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 31, 2014 | Bosch Water Heaters
Dec 02, 2014 | Water Heaters
Sep 19, 2014 | Water Heaters
Sep 21, 2013 | Water Heaters
Jan 27, 2011 | Bosch Water Heaters
Jan 21, 2011 | Bosch Water Heaters
Dec 06, 2010 | Bosch Water Heaters
Jan 08, 2010 | Water Flexcon WH8S Potable Heater...
Nov 29, 2009 | Water Heaters
3,476 people viewed this question
Usually answered in minutes!