Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
The existing inducer fan is making some loud sounds when comming on. The existing heating system is locking out. When testing and jumpering out the blocked vent switch the system comes on. The existing flue serving the existing heating system is open. The system will fire normally for serveral days and lock out again. Are the blocked vent switches only good for sensing only one flue gas failure or should it be replaced. Also could the existing fan induced motor be defective and is not removing all the flue gases causing the blocked vent switch sensor to open and lock down the heating system. I thank you in advance for your attention to this matter.
If it is making noise, the motor may be ready to give out. The pressure switch could be faulty, but it sounds as if you need to replace the vent motor if you can find a replacement. Otherwise you've got to replace the entire vent.
Posted on Feb 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2015 | Heating & Cooling
on Dec 04, 2009 | Heating & Cooling
Dec 15, 2013 | Carrier 3 Ton 13 Seer Commercial Gas Pack...
Jan 01, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Mar 17, 2009 | Goodman GMS90703BXA Heater
Jan 26, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 06, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 03, 2008 | Carrier Heating & Cooling
215 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: