Question about Emerson Quiet Kool 6GC53 Air Conditioner
An air conditioner of this type always has standing water sitting in the base-tray of the machine as it's running. They're designed to work that way. However, if the unit leans slightly in toward the inside of your house, then the water in the tray can be deeper than it should and/or add extra humidity to the inside air. These units are designed to be installed so that they lean slightly to the _outside_ of the window or wall-hole where they are mounted. This way the standing water drains off to the ground outside and isn't so deep on the inside of the unit that it adds too much humidity to the inside air. Check the mounting of this unit to make sure it leans slightly toward the outside. Also verify that any notch or drain hole on the outside end of the unit, intended to guide draining water, is not clogged with debris (which could also cause the standing water in the unit to be at too high a level). Also verify that the "vent" is closed, if this unit is equipped with said vent opening. An open vent panel can allow humid outside air inside as the unit is running. Hope this helps! ;)
Posted on Aug 05, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 11, 2017 | Dehumidifiers
Jul 29, 2015 | Dehumidifiers
Jan 04, 2015 | Humidifiers
Jan 03, 2015 | Heating & Cooling
Jun 11, 2014 | Friedrich Heating & Cooling
Jul 08, 2012 | Dometic Rooftop RV Air Conditioner
Jul 17, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Jan 02, 2010 | Whirlpool 75-Pint Dehumidifier
Sep 29, 2009 | GE Heating & Cooling
302 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: