Question about Heating & Cooling
The outside unit was staying on all the time and the problem seemed to be the contactor not releasing. I replaced the exact contactor and now the contactor will not connectwhen heat or air is called for - so now the unit will not come on? Is it something Iam missing?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 08, 2015 | Goodman Heating & Cooling
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Jan 25, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Aug 31, 2013 | Goodman CKL30AR30 Air Conditioner
Aug 17, 2012 | Goodman Heating & Cooling
May 31, 2011 | Heating & Cooling
May 30, 2011 | Goodman Heating & Cooling
Jul 09, 2010 | Goodman CLJ30AR32 Air Conditioner
Jun 24, 2009 | Goodman CLQ36AR49 Air Conditioner
Nov 10, 2008 | Goodman PHKJ048-1 Air Conditioner
Apr 26, 2017 | Heating & Cooling
91 people viewed this question
Usually answered in minutes!