Question about Heating & Cooling
If its opening and closing it sounds to me like a loose wire nut on your 24volts to your water solenoid valve. The only time that the humidifier should come on is in heating mode and then when the furnace gets up to temp and the blower starts. If furnace is older it will have a current sensing relay located in the blower compartment with a plastic box and two wires coming off of it.One of the blower wires( generally RED for low speed) should be going through that sensing relay.If you have some slack in that blower wire try wrapping it around that sensing relay a few times. I would chek all my wire nuts first though before you do the sensing relay. David
Posted on Feb 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 30, 2013 | Aprilaire 700 Humidifier
Nov 28, 2012 | Aprilaire 600 Humidifier
Nov 15, 2010 | Aprilaire 700 Humidifier
Feb 17, 2010 | Aprilaire 550 Humidifier
Dec 31, 2009 | Aprilaire 558 Humidifier
Dec 13, 2009 | Aprilaire 700 Humidifier
Feb 25, 2009 | Aprilaire 700 Humidifier
Aug 27, 2008 | Aprilaire 600 Humidifier
Dec 24, 2007 | Aprilaire 700 Humidifier
Nov 28, 2007 | Aprilaire 550 Humidifier
98 people viewed this question
Usually answered in minutes!