Question about Heating & Cooling
If its opening and closing it sounds to me like a loose wire nut on your 24volts to your water solenoid valve. The only time that the humidifier should come on is in heating mode and then when the furnace gets up to temp and the blower starts. If furnace is older it will have a current sensing relay located in the blower compartment with a plastic box and two wires coming off of it.One of the blower wires( generally RED for low speed) should be going through that sensing relay.If you have some slack in that blower wire try wrapping it around that sensing relay a few times. I would chek all my wire nuts first though before you do the sensing relay. David
Posted on Feb 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 21, 2014 | Aprilaire 4087 Replacement Float Valve...
Apr 19, 2011 | Amana Heating & Cooling
Mar 02, 2011 | Heating & Cooling
Feb 27, 2011 | Heating & Cooling
Jan 28, 2011 | Heating & Cooling
Dec 28, 2010 | Heating & Cooling
Dec 24, 2010 | Heating & Cooling
Nov 22, 2010 | Heating & Cooling
Dec 13, 2009 | Amana PTC074B25AE Electric Heat Air...
Apr 22, 2008 | Heating & Cooling
98 people viewed this question
Usually answered in minutes!