Question about Ruud Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Feb 19, 2016 | Carrier Heating & Cooling
Sep 11, 2014 | Heating & Cooling
Oct 18, 2013 | AO Smith Carrier HC24AU725A Rheem Rudd...
Oct 10, 2013 | Goodman Heating & Cooling
Dec 31, 2012 | Fasco Furnace Draft Inducer Heil Quaker...
Jan 06, 2011 | Goodman Heating & Cooling
Feb 15, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 10, 2009 | Heating & Cooling
Not having a make or model number, I can only give you generic information. However if you add more info, others and myself can give you a better diagnosis.
In order for a furnace to start that has an inducer motor, the thermostat must call for heat. Then the circuit board will flash rapidly. There should be power from the board up to the inducer motor. If there is too much resistance, the blower motor or pressure switch(s) will shut down the unit. I would suggest that if you can spin the inducer motor by hand, check for resistance. It may be frozen up or there may be water in the housing not allowing the blower to turn. Check for a plugged water drain at the bottom of the blower housing and make sure it drains. If the inducer blower does not even try to start, you will need to check for voltage from the circuit board. Not knowing for what you have for a model, I am unable to tell you if you should be checking for AC or DC voltage.
Get back to us as soon as you can with more info.
Thank you for your patience.
Oct 18, 2007 | Heating & Cooling
103 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: